Pill stamp press factory by SZ-pharma: Clean room (aseptic room) should meet the standard requirements: The aseptic room should have good lighting, avoid moisture and stay away from contaminated areas. The area is generally not more than 10㎡, not less than 5㎡and the height shall not exceed 2.4m. It is composed of 1-2 buffer rooms and operation rooms (The doors of the operation room and buffer room should not be directly opposite); Transfer window with sterilizing function between handling room and buffer room. In the buffer room, there should be a wash sink, sterile clothes, slippers and wardrobe, etc., there should not be other debris placed. The wall of the sterile room should be smooth and smooth, and can withstand cleaning and disinfection. Read more information on pharma machinery.
Air filter refers to the air filter device, which is generally used in clean workshop, clean workshop, laboratory and clean room, or used for dust prevention of electronic machinery communication equipment. There are primary filter, medium efficiency filter, high efficiency filter and sub high efficiency model. Different models have different standards and performance. The comprehensive performance test of clean room includes: Wind speed, air volume (ventilation frequency), temperature and relative humidity, suspended particle number, planktonic bacteria, settling bacteria, static pressure difference, illumination, noise, air flow pattern, self purification time, high-efficiency filter leak detection, total bacterial colonies in the air, total bacterial colonies on the surface of the worktable, total bacterial colonies on the surface of the worktable, total bacterial colonies on the surface of workers’ hands, etc.
Automatic industrial paper folding machine, small desktop origami paper folding machine is suitable for paper folding in various ways. It has a reasonable structure. It uses a large rubber wheel to feed paper. It has accurate separation, stable performance, convenient operation and high efficiency. The minimum folded width is 30mm, which is especially suitable for the folding of the instructions for drugs and cosmetics with small width.Want to konw more, contact SZ pharma, one of the most professional paper folding machine manufacturers & suppliers in China.
Efficiency of Equipment: Some equipment, such as electronics and mechanical components, require specific humidity levels to function correctly. Maintaining the right humidity levels in clean rooms ensures optimal performance and longevity of these critical pieces of equipment. How to Maintain Optimal Humidity Levels in Clean Rooms? To maintain optimal humidity levels in clean rooms, consider the following steps: Install a Dehumidifier: A dehumidifier is an essential tool for maintaining proper humidity levels in clean rooms. It removes excess moisture from the air, keeping humidity levels within the desired range. Choose a dehumidifier based on the size of your clean room and the relative humidity requirements you need to meet.
The clean room workshop is also called the dust free workshop, gmp cleanroom, the industrial clean room (Clean Room) and the dust free room. It refers to the removal of pollutants such as particles, harmful air and bacteria in the air within a certain space, and the indoor temperature,cleanliness, indoor pressure, air velocity and air distribution, noise and vibration, lighting and static control. A specially designed clean room for a particular requirement. That is to say, no matter how the extemal air conditions change, the clean room can maintain the characteristics of cleanliness temperature and humidity and pressure.
The detection of air volume and wind speed must be carried out first, and all effects of purified air conditioning must be obtained under the designed air volume and wind speed. Before air volume detection, it is necessary to check whether the fan operates normally, whether all components in the system are installed correctly and whether there are obstacles (such as whether the filter is blocked or blocked). All valves should be fixed at a certain opening position, and the size of the measured air outlet and air duct must be measured. For the turbulent flow clean room, the air supply volume shall be determined by the air outlet method or air duct method. See Item 6, 7 and 8 respectively. For the air outlet without filter, the method in Appendix I of the current national standard code for construction and acceptance of ventilation and air conditioning engineering (gbj243) can be implemented.
Airflow is the most important factor in controlling cleanliness and temperature and humidity, and it also has some influence on noise. Therefore, the wind speed measurement is the first step in the clean room test. The purpose of the wind speed measurement is to confirm that the air flow sent by the filter meets the design specifications, and the second is to confirm the uniformity of the air flow. In some occasions, due to site restrictions, the indoor ventilation volume must also be converted by multiplying the wind speed by the outlet area. See extra info at https://www.sz-pharma.com/.
Quality pharma clean room manufacturer: Today (Suzhou Pharma Machinery Co., Ltd.) will introduce to you, clean room airflow and influencing factors. There are many factors affecting the airflow in the clean room, such as process equipment, personnel, clean room assembly materials, lighting fixtures, etc. At the same time, the distribution point of airflow above the production equipment should also be considered.
The frame of the clean shed can be generally divided into three types: stainless steel square pass, varnished iron square pass and industrial aluminum profiles. The top and the top can be made of stainless steel steel plate, lacquered cold plastic steel plate, anti-static mesh curtain and acrylic plexiglass and other materials. Anti-static mesh curtains or plexiglass are generally used around, and FFU clean air supply units are used in the air supply unit.